Kings Electrical and Air Conditioning promises customer service that exceeds the expectations of Lauderdale Lakes FL residents.
Call us now at: (954) 753-9436 . We'd love the opportunity to earn your business as we have with your neighbors in Lauderdale Lakes FL.
for Lauderdale Lakes, FL
Our Reviews by City
Hello Rosemarie! Today we came out and did an electrical inspection on your home. Upon further investigation we noticed that a lot of the receptacles within the home are ready to be changed. Because of this we highly recommend that you do a device upgrade throughout your whole home. This includes swapping out all outlet and switches for new high grade ones. We also noticed that in your bathroom and kitchen there are a couple of receptacles that need to be converted to GFCI protected ones. Another thing we noticed was that In your panel you have uneven voltage readings. A phase reads about 118v and b phase is reading near 116v which is lower than the recommended average. Please contact FPL to check that their side is providing the proper voltage to your home and if still there is no change consider changing out the main breaker that is feeding the indoor panel. Thank your for trusting in us today and we look forward to servicing you in the near future. Your Service Electrician Je
Job # SHMNP123A58B2-1 Approval # PHM 0725171 Supply and install new 150A indoor electrical panel. Panel is extremely old and needs to be replaced. Old breakers and connections are causing power issues inside home. Supply and install outdoor 150A main breaker panel. Main breaker panel is a very old brand and is losing its strength from years of use.
Already Sold to job ending in 6003
Replace (1) 125 amps main lug indoor panel Pull permit and get inspection
Evaporator coil frozen causing water dripping on the floor. Freon was low (80 psi on low side). Added 2 lbs 410A to get it run temporary. Need installation team come back to check for the leaks
Supply and install 2.0 ton Rheem split system Supply and install safety float switch on AHU Supply and install New Non-Programmable thermostat Supply and install condensate pump on unit. Supply and install hurricane rated tie down straps on condenser on the roof. 10 year manufacturer's warranty 1 year KINGS labor warranty 1 year RCC club AC maintenance included. Crane will be needed. Permit are required
Replace 30ft cloth wires on attic by Romex wires
1)â€”â€”Replace freezer outlet.
Install 2 new fluorescent fixtures in bathroom.