Kings Electrical and Air Conditioning promises customer service that exceeds the expectations of Lauderhill FL residents.
Call us now at: 954-753-9436. We’d love the opportunity to earn your business as we have with your neighbors in Lauderhill FL.
for Lauderhill, FL
Our Reviews by City
Dukes - Lauderhill, FL
Completely satisfied with service.
Trustworthy! Great Service!!!
Lorde - Lauderhill, FL
Second time using them. Great customer service. Organized and knowledgeable. A local company I can trust. The Lorde’s says yes to the KINGS 👑
Dukes - Lauderhill, FL
Nick arrived on time, completed the task and cleaned the area. I would recommend him.
trini - Lauderhill, FL
Paul was a fabulous electrician. Very methodical, experienced, and thorough!
Sally - Lauderhill, FL
Ruslam - Lauderhill, FL
1)â€”â€”Add pig tail to 2 wires on double tapped breaker to make it 1 wire on the breaker.
1 year AC RCC. 3 times/year
Diagnosis level 1 Supply and install (1) power cord for disposal
Reset GFCi breaker
Replace Exterior 200 amp main breaker panel
AC tune up
1)-----Extend circuit from inside outlet to exterior jucntion box. 2)-----Install weather resistant GFI and bubble cover at exterior jucntion box. 3)-----Remove other exterior outlet. 4)-----Install new receptacle and bubble cover.
Supply and install (3) white outdoor photocell lights (incadecent) Install (1) dimmer
1)-----Remove 200 amp main breaker panel. 2)----Replace with new 8/16 circuit 200 amp main breaker feed thru panel. 3)-----Label panel and clean area. NOTE: CUSTOMER IS AWARE THAT THIS MAY OR MAY NOT FIX THE ISSUE OF MAIN TRIPPING. NO GAURANTEE.
1)-----Remove bad 200 amp main breaker. 2)-----Supply and install new 200 amp main breaker.
Water heater trips when elements kick in. Breaker is getting power and not tripping unless water heater is connected
1)-----Remove 200 amp main breaker outdoor enclosure. 2)-----Replace with new 200 amp 8/16 circuit outdoor main breaker panel. 3)-----Install whole house surge protector. 4)-----Update grounding: Install 2 new ground rods, 1 water pipe ground and 1 low voltage ground bridge interconnected with #4 gauge bare copper wire. 5)-----Label panel and clean area.
Double tapping removed
Supply and install new 150amp GE Panel Supply and install new 3.0 ton split system Supply and install new non programmable thermostat 10 year manufactures warranty on all parts 1 year warranty on labor 1 year main program on new unit.
1) Troubleshoot kitchen, dining and stairwell lighting circuits. 2) Found 3 way systems wired incorrectly at each location. 3) Rewired each system so that lights could be switched at 2 locations in each area.
Provided up front flat-rate price for troubleshooting and repairing buzzing panel.
Hardwire hot water heater.
Replaced old landscape lights with green LED permaposts. Tech also installed new green lighting fixtures.
Replaced existing dimmer with Decorah single pole switch.
Install new electric riser and weather head and hub