Kings Electrical and Air Conditioning promises customer service that exceeds the expectations of Pembroke Pines FL residents.
Call us now at: 954-753-9436. We’d love the opportunity to earn your business as we have with your neighbors in Pembroke Pines FL.
for Pembroke Pines, FL
Our Reviews by City
Harrell - Pembroke Pines, FL
Professional, knowledgeable, pleasant.
Davis - Pembroke Pines, FL
EXCELLENT, he is a great value to your company
Bronsburg - Pembroke Pines, FL
Efficiency and professional well worth the price
SamonsRobert - Pembroke Pines, FL
Kept me in the loop, they were prompt professional and tidy. What more can be said! Great Job!
Very professional knows his work
Rodriguez - Pembroke Pines, FL
Scott - Pembroke Pines, FL
Got the job done quickly. Very polite. Didn’t try to sell me things I didn’t need or want.
Mitchell - Pembroke Pines, FL
Nick is great! He is efficient, patient and easy to work with! Very happy I found them!!
Haxton - Pembroke Pines, FL
Tamer - Pembroke Pines, FL
Robert - Pembroke Pines, FL
Great job by Nick
David - Pembroke Pines, FL
Nick took care of all my issues, he explained the process and the options right up front, great job and my issue was fixed in no time. The folks on the phone are super friendly, great electricians to work with.
Several small projects
Scott - Pembroke Pines, FL
I hired Kings for several small projects. The workmanship was good, the price higher than I expected.
Ana - Pembroke Pines, FL
I had this problem since May, getting different opinions but Philip really knows his job, solved my problem. He is very professional. I will recommend this company without a doubt.thank you.
Good work, good service
Sergio - Pembroke Pines, FL
This is the second time using your services. Both times very satisfied
Excellent professional service
Ron - Pembroke Pines, FL
Simply the best and the best electrical and ac service in south fl
Cut out and clean evaporator coil outside. Reinstall the coil, check leaks and charge system
AC 18 points check up for 2 systems
Remove double tapping wires according to inspection report
1)â€”â€”Remove and replace GFI outlet in garage with 20 amp weather resistant GFI. 2)â€”â€”Remove outlet and cover in back of home and replace with 20 amp weather resistant outlet and bubble cover.
Hello! Thank you for choosing Kings electric & A/C for your electrical needs and savings. Today I was called out because you would like (4) fixtures removed and (2) JBOXS added safely because your going to install recessed lights yourself. I gave you the option to do just that today, and the job was completed as asked. If you have any questions or concerns please reach out and weâ€™ll be able to help out. Your electrical technician, Xavier
Hello! Thank you for choosing Kings electric & A/C for your electrical upgrades today. You were having problems with your challenger 125 amp main lug panel. I gave you (2) options today and you decided to go with the (BEST) option. I replaced the existing panel with a brand new one, added a surge protector, and also labeled the panel in Spanish for your convenience. All the work was tested and everything is working 100%. Thank you again and if you have any questions please reach out. Your electrical technician, Xavier
Hello, thank you for choosing Kings electric & a/c for your electrical upgrades. Today when I got to the home I was explained about the things that are occurring with the breakers and pool pump outside. I suggested (3) different options and you chose the â€œBestâ€option. All breakers and timers have been replaced and also I added (2) surge protectors for both panels in the home, If any questions or concerns please reach out. Your electrical technician, Xavier
1)â€”â€”Remove and cap off fixture in living room.
AC Red carpet club
1)â€”â€”Remove 5 existing fluorescent fixtures. 2)â€”â€”Install junction box at both switch lines inside soffits.
1)â€”â€”Remove faulty 60 amp breaker for tankless water heater. 2)â€”â€”Install new 70 amp breaker.
Replace (1) 150 amps main lug indoor Challenger panel by GE panel Replace (1) 150 amps main breaker outdoor Challenger panel by GE Permit fee will be passed through customer if requested
Diagnosis lights in kitchen not working Found: bad dimmer switch Solution: replace (1) dimmer switch with 1 year warranty
1 year Rcc club for AC
1)â€”â€”Extend switch line using wire mold conduit and fan rated junction from existing switched outlet to desired location of fan at 3 locations. (Living room, Bedroom 1 and 2) 2)â€”â€”Assemble and install 3 customer supplied fans.
Install customer supplied chandelier (18 ft) Replace (4) Hi Hats with LED bulbs (customer supplied) Install customer supplied outdoor fan Raise fan in kitchen 6 inches with new Gold rod Install customer fan in 2nd floor bedroom
Supply and install new indoor 150amp electrical panel.
Supply and install new copper lines from new outdoor condenser to edge of building slab. The existing copper lines have leak somewhere underground or inside the building between the air handler unit in the unit and the outside condensing unit. Original contract includes replacing the existing equipment to the EXISTING copper lines, electrical and condensate drain systems.
Perform 2nd visit Recommend UV light kit to improve air quality and prevent mold growth in the air handler
Install (1) round fixture customer supplied
1)â€”â€”Remove indoor 200 amp main lug circuit panel. 2)â€”â€”Install new indoor 200 amp 20/40 circuit main lug panel. 3)â€”â€”Label, rough patch and clean area.
AC leaking Perform 2nd Rcc visit
Remove and discard existing indoor panel Supply and install (1) 200 amps 20/40 circuits indoor panel Replace aluminum feeders from outdoor panel to indoor panel by copper and replace PVC pipe to 2â€ diameter also. *** Remove and discard existing outdoor panel Supply and install (1) 200 amps 8/16 branch circuit main breaker Re-run all pool equipment electrical into new panel including pool pump, pool light, hot tub. Also supply and install (2) 50 amps breaker for heat pump and hot tub for future installation Upgrade grounding system up-to-code Permit fee will be passed through customer if needed
1)â€”â€”Remove 150 amp FEDERAL PACIFIC main breaker circuit panel. 2)â€”â€”Install new 150 amp GE 8/16 circuit main breaker panel. 3)â€”â€”Supply and Install 60 amp fused AC disconnect.
Tech Found that pump was bad