Kings Electrical and Air Conditioning promises customer service that exceeds the expectations of Pompano Beach FL residents.
Call us now at: 954-753-9436. We’d love the opportunity to earn your business as we have with your neighbors in Pompano Beach FL.
for Pompano Beach, FL
Our Reviews by City
Gillyard - Pompano Beach, FL
This is our first time working with Kings Electrical and I must say will use them again! The service was excellent and the upfront pricing was amazing! There was no guess work in what will be done in the scope of work. The technician was professional and follow all safety protocols for COVID.
Great service Good explanation
Pigeon - Pompano Beach, FL
ZambranoCristian - Pompano Beach, FL
Top quality service. Quality work and reasonable prices.
Conroy - Pompano Beach, FL
I have used Kings Electrical for several years, including major electrical panel change outs, as well as alarm system installation, ceiling fan installation, etc. Kings are prompt, tidy and the work is exemplary. I will call them for any other electrical work that I require.
Panarotti - Pompano Beach, FL
Pigeon - Pompano Beach, FL
United - Pompano Beach, FL
Gean-BaptisteMichel - Pompano Beach, FL
Could not be happier
Pilot - Pompano Beach, FL
King’s Electric gave us too rate service. Nick got everything we needed completed and the work is excellent. Nice to have a company that takes pride in what they do.
Tremblay - Pompano Beach, FL
Great company and I would use them again and reccomend them to anyone else.
Great Service Jason is perfect
Berthiaume - Pompano Beach, FL
Smith - Pompano Beach, FL
They show up when they say they will and this is so rare in the state of Florida.
Top quality service. Quality work and reasonable prices.
Conroy - Pompano Beach, FL
Selmonsky - Pompano Beach, FL
Showed up on time, was knowledgable and got right to the repair and checked everything worked and cleaned up his area and got it done in a pretty timely fashion. Good experience.
Great service. Quite pricey
Schmidt - Pompano Beach, FL
I think for $2,000 for two hrs of work for one person is quite observant.
Run Circuit extension from existing outlet with power to existing outlet that has lost power. -Install outdoor post head lamp
Both existing air conditioning units on the roof servicing the warehouse are past their useful life expectancy. Both units are 14 years old. The units use R-22 Freon which is outdated and no longer permitted. Not environmentally friendly. The units have metal condensate pans which are rusting and leaking. The coil in one of the units has a leak someplace and causes the system to freeze up then defrost causing water to leak through the ceiling. The other unit has a defective condenser fan motor causing the system to overheat and shut-off. Both units are old and compromised and should be replaced.
A) Warehouse Area * Replace existing 7.5-ton system located on warehouse area. Installation of one new 7.5-ton America standard RTU to match exist curb. * Including new motorized damper, programable thermostat and dual cut off safety overflow switch. * Installation of one new duct system for 7.5-ton system with minimum duct drop down and 5 grilles in the plenum. * Return drop down with screen mesh. * System will have included one smoke detector on supply side with key station. B) Office Area * Installation of one (1) new Goodman 5-ton RTU including new curb, electric heater, programable thermostat, motorized damper, PVC drain and dual cut off safety overflow switch. *System will be ducted to existing supply and return main lines going to east offices. We will add total of 3 return drops. Permits & Inspections included. NOTE: All roofing penetrations, repairs, engineering (if needed) by owner. NOTE: Subject to building department review and approval.
Supply and install one (1) new 200-amp, 3-phase, 120/240-volt, 42-ckt interior electrical panel with sub-metering device. Power to originate from the existing buss-duct system in bay #3. Remove three (3) existing 1-phase electrical panels in Bay #3 Identify the existing circuits from the office area in Bay #3 and re-circuit them to the new 200-amp electrical service. Provide all conduit, wire and junction boxes required to re-route the existing circuits to the new panel. Disconnect and cap-off all old office circuits no longer being used. Relocate wiring to "house lights" with timers from Bay #3 to Bay #2 electrical panel. Includes wiring to new RTU units on roof. Existing office wiring, fixtures, switches, etc., to remain "as-is". Subject to the final approval of the building department.
Warehouse Area * Supply and install one (1) 10-ton system located on warehouse area. Installation of one new 10-ton America standard RTU to match exist curb. * Including new motorized damper, programable thermostat and dual cut off safety overflow switch. * Installation of one new 50 linear ft. of horizontal duct system for 10-ton system with minimum duct drop down and 10 grills in the plenum. * Include 3-phase power wiring and electrical disconnect at unit. * Include low voltage wiring for thermostat. * Return drop down with screen mesh. * System will have included one smoke detector on supply side with key station. NOTE: All roofing penetrations, repairs, engineering (if needed) by owner. NOTE: Subject to building department review and approval.
Supply and install one (1) new 200-amp, 3-phase, 120/240-volt, 42-ckt interior electrical panel with sub-metering device. Power to originate from the existing buss-duct system in bay #2. Identify the existing circuits from the office area in Bay #1 and re-circuit them to the new 200-amp electrical service. Provide all conduit, wire and junction boxes required to re-route the existing circuits to the new panel. Disconnect and cap-off all old office circuits no longer being used. Includes wiring to new RTU units on roof. Existing office wiring, fixtures, switches, etc, to remain "as-is". Subject to the final approval of the building department.
Dear customer. Weâ€™re happy to give you the estimate to correct the issues that has been addressed on inspection report â€” Replace (1) open neutral combo switch-outlet by 2 separate switch and GFCI outlet in master bathroom â€” Remove the regular outlet and repair wiring issues in 2nd bathroom. â€” Diagnosis (3) outlet in two different areas (guest bedroom and dining room) donâ€™t have power, not including run new wires if they are interrupted â€” Repair (1) open ground outlet in garage conversion room â€” Add pool pump switch and install bubble cover â€” Run new ground wire inside the conduit for pool pump, gas line and water pipe Thank you for choosing us and feel free to reach out for more details **********Jason - Kings Electric & AC**********
Upon arrival noticed two units with no power. Turn breaker at buss duct electric panel & units kicked on. Package unit running but in bad shape evaporate coil is dirty and has dust everywhere it also needs at AX35 belt a coil cleaning also system on cooling 2nd stage . For existing split system 7 ton in Bay #2 Unit slight under charged charged two lbs of 410 unit now has subcool of 12 degree . Completed check unit is cooling will need adjustment with returns since we eliminated Bay #1 ductwork to separate system. Also survey Bay #1 curb and a/h possible location & where we will cut in roof jack and stand.
WO 201113-00272 Problem: AC unit C-1 is not cooling. Temperature reads 86 ( please check all units in C building for proper operations) Make : Carrier Model : FA4CNC048 Serial : 0307A87748 Type : Air Handler Make : Carrier Model :38CKC047300 Serial : 3301E15141 Type : Condenser Tech Notes : Found outdoor unit not running . Upon further inspection found run cap with bad mfd. Replaced run cap 50mfd and added 3 lbs of 422d replacement. Unit are in bad shape but still functioning at this time. Bad filters as well 22x22 x1 . Other unit are running accordingly at this time Solution : Replaced 50mfd Capacitor and added 3 lbs of 422d replacement gas. Replaced Filter. Checked all other units. All other units are working well.
One of the compressor is low on freon. Need add 3 lbs of R22 replacement refrigerant Recommend add leak stopper due to the corrosion on copper lines to seal the leak if possible Total amount will be deducted toward new AC replacement
Replace (1) 2 ton AC split system with new high efficiency system. 10 years warranty from manufacturer and one year warranty from Kings Permit fees Included
Replace bad switch ( customer provided)
Replace (1) 35/5 mfd dual capacitor Replace (1) 24v contactor Total amount will be deducted toward new Ac replacement installed by Kings
Happy Monday Mr Bernon! I was extremely grateful to be able to help you out last minute with your lighting situation. I was able to diagnose and resolve your issue with your lighting circuit plus put in two new switches as well. Pleasure in meeting you. Your Service Electrician Jeahn Bermudez
Perform 1st rcc visit Clean out drain pan and seal with silicone No warranty for the sealant If the leaks occur again, we will credit back half of the amount toward coil replacement
Diagnosis one room doesnâ€™t get cool air, found out the damper was closed, opened plenum and opened damper AC leaking at warehouse unit, found drain pipe clogged, cleared out drain pipe but recommend fix the drain line to prevent clogged again : Cut-out and re-support (1) drain pipe to get proper water flow
Diagnosis dryer outlet not working Replace (1) 10-3 dryer outlet
Hey! Thank you for calling Kings Electric & A/C for your electrical repairs. Today I came out because youâ€™re having issues with the power for your lights and some outlets as well. After troubleshooting and opening up the outlets I saw you had burned wire and a box as well. I had to rewire from the meter to the outlet to replace the burned wire. I also replaced 2 burned out outlets you had as well. Iâ€™m glad to inform you that everything is working and has power once again. If you have any questions or concerns, please reach out. Your electrical technician, Xavier
Diagnosis one room doesnâ€™t get cool air, found out the damper was closed, opened plenum and opened damper AC leaking at warehouse unit, found drain pipe clogged, cleared out drain pipe but recommend fix the drain line to prevent clogged again
One Bay lost power Warranty previous job
Install (1) photocell customer supplied Diagnosis (1) outside not working in bay 38 Found losing breaker, fixed it
Run 100A 3P Circuit appox 25 ft from panel to machine. Supply and install 3P Breaker. Hardwire Machine. Customer will be supplying transformer with this estimate.
Check electrical wires to make sure they are dead and cap them off
Hey Michelle! Thank you for calling Kings Electric and AC for your electrical repairs. Today we were glad to be able to help you out with swapping out your 30 amp outlet that was incorrect for your Dryer. We installed a NEMA 14-30 outlet for your dryer and made sure everything was working correctly before leaving. Your Electrical Service Technicians, Jeahn & Xavier
Hey tony! Thanks for calling Kings electric & a/c for your electrical upgrades. Today We were called because youâ€™ll like to replace (7) outlets and install (7) new decor outlets, also you wanted to switch out (2) fans one in the kitchen and the other one on the balcony. To continue you wanted to install (4) surface mounted light fixture and wanted us to put face plates on all devices in your home. If you have any questions or concerns, please give us a call. We hope you have a great Day! Your electrical technician, Jeahn & Xavier