Kings Electrical and Air Conditioning promises customer service that exceeds the expectations of Davie FL residents.
Call us now at: (954) 753-9436 . We'd love the opportunity to earn your business as we have with your neighbors in Davie FL.
for Davie, FL
Our Reviews by City
Jason with Kings Electric
Zisser - Davie, FL
Randolph - Davie, FL
He was SUPER Wonderful Awesome 👍😃
Great service and fast too.
Stang - Davie, FL
Great service, kept in touch so I knew when the service person was coming and completed repairs within a few hours of my call.
Great service, knowledgeable
Schreiber - Davie, FL
Kings never lets me down! They show up on time, they are thorough and great at troubleshooting. I e referred them to family, friends and customers .
Excellent and timely service
Roa - Davie, FL
Great service and nice people
Sclar - Davie, FL
Would recomment tonfreinds sbd family!
Stokes - Davie, FL
Assan - Davie, FL
Phil is good
Great work...clean, effective, time conscious.
Turano - Davie, FL
I recommend your company and Nick, to my family and friends.
PUSIC - Davie, FL
Quality work! Professional attitude
Turano - Davie, FL
Hassle free and Reliable Service
Jones - Davie, FL
King’s Electric is the only Electric Company we use. Nick has done several big installations at our home and we have had zero complaints or problems. The staff is Professional and stands behind their work. Great experience!
Turano - Davie, FL
Luna - Davie, FL
Nick was amazing
Stang - Davie, FL
Hello Roanne! Thank you for trusting in Kings Electric with your electrical needs. Today we came out to inspect your grounding system in regards to what can be covered and and what must be left visual when the new landscape is installed. We came to a conclusion that youâ€™ll be fine if they rise up 5 - 6" which will still allow some visual of the grounding rods and acorn/clamps. Just make sure that in the process they donâ€™t compromise the wire. It was a pleasure servicing you and we look forward to helping you out in the near future. Your Service Electrician Jeahn Bermudez
Install new 20A outlet in kitchen
SHMP123D128E-2 Approved by Lapino - Extend circuit from existing indoor outlet in living room, approximately 40ft underground - Supply and install (1) photocell - Clean the area, customer is responsible for putting sod over the area
Replace (1) used 30A 2 pole breaker Total amount will be deducted toward new panel and AC replacement Replace (1) float switch
Replace (1) regular outlet Inspect fan switches and wiring inside fan box
Replace Circuit board / Xfermer. Parts under warranty.
We were dispatched for the following Had flooding down C, D, E, Y, and H aisles, little in B aisle last week. had roofing company here but they say no roof leaks. DM requesting maintenance on ac in the main building. Also, have a small leak on 2nd floor of 2nd building in front of unit A238. The following was found : Make : Trane Model : 4TEC3F42C1000AA Serial : 93554542V Delta -18 Solution : Replaced Run Capacitor 45+5 Installed Hard Start kit. Make : Carrier Model : 24ABC636A300 Serial : 0513E06859 Delta - 20 Solution : Replaced Run Cap 45+5 Make : Carrier Model : 24ABC636A00 Serial : 0513E06901 Delta - 20 Solution : Replace Run Cap 45+5 and Replaced Thermostat. Tech Notes : When I arrived I noticed multiple units not working as mentioned above. All 3 AC's had bad run cap's and one unit had a bad thermostat as well. Also put a hard start kit on one compressor. All 3 units now are working properly.
Diagnosis hot water heater not working Replace (1) 2 pole 30 amps breaker Dedicate 240v lines for water heater which was bad
WO:20111300272 Problem: Blowing hot air Unit A122 or 1122 A122 or 1122 Brand :Carrier Model : FV4CNF005 Serial : 2817F19172 Type : Air Handler Brand : Carrier Model : 24ACC648BA300 Serial : 0218E15806 Type : Condenser Tech Notes : Upon arrival located filter that got clogged into coil. Unit short cycled also Added 2 lbs of 410A. Solution : Found clogged filter at Air Handler Coil and removed and replaced.
Upon arrival P.S Employee directed me to correct areas building C where slight smell in trunk line due to water damage . After verifying which systems go where noticed two systems that had bad delta T . System A Coil in bad shape filters have not been changed over two years. Corre
Hello Meghan! Thank you for having us stop by today to check on your your commercial signs! Upon review we concluded that the LED driver that powers your Led lights in the sign is receiver proper power. That being said, the issue with your lights not turning on has to lie in the led drivers the sign company installed. We left the power manually on so that the Sign installers can trouble shoot their issues. Please let us know if there are any further issues with the timer. It was a pleasure servicing you, Your service Electrician Jeahn C Bermudez
Run new conduit and wire for AC Disconnect on roof from 2nd floor existing electrical panel to roof. Access must be given from 3rd and 4th floor apartments in order to run conduit through. Roof Penetration must be patched by condo association roofer. Patching and painting (If needed) to be done by others. Permit fee's included.
(1) year red carpet club, 2 visits a year Perform 1st visit
Replace (1) Trane TZON1050AC52ZAA thermostat
Clean condenser coil Relocate dryer vent away from condenser unit
Replace (1) 2.5 ton AC split system with new high efficiency system. 10 years warranty from manufacturer and one year warranty from Kings Need crane to remove the existing equipment and bring new condenser up to the roof Permit fee will be passed through customer if requested. Estimated $500 Note: if system needs to be replaced within 6 months since installing leak stop, 1/2 amounts of the amount will be credited back toward new system AC
Supply and install (1) leak stopper Add 1 lbs of Freon
Hey Aaron! Thank you for calling Kings Electric & A/C for your electrical repairs. Today I was called because youâ€™re having issue with your GFCI. I have great news I was able to replace both GFCI and I added a whole home surge protector for your electrical panel. Everything is working great once again. If you have any questions or concerns, please reach out. Your electrical technician, Xavier
Water filter needs power adapter from manufacturer
Hey ED! Thank you for calling Kings electric & a/c for your electrical upgrades to your home. Iâ€™m glad to inform you that all the work is done and everything is working 100% once again! We added a brand new 200 amp main lug panel with itâ€™s own surge protector, also brand new breakers and connections. Finally both a/c disconnects, grounding system, surge protector for outside panel, and rewire of sprinkler pump was done. Thank you for allowing us to come to your home and do this work. We hope you have a great night! If you have any questions or concerns, please reach out. Your electrical technician, Jeahn & Xavy
Found that there may be a j-box in between panel and roof. Need to revisit.
Hey Edward! Thank you for calling kings electric & a/c for your electrical upgrades. Today I came out because youâ€™re having issues with your sprinkler system and the power that is going to it. As I was troubleshooting through your home opening up all panels and disconnects, Iâ€™ve come to conclusion that your electrical issues are beyond just the sprinkler system. I explained all (4) options How we can get everything 100% once again. I hope to hear from you soon! Your electrical technician, Xavier
Renew (1) year rcc, 2 visits/year
Hello! thank for choosing kings electric & a/c for your electrical upgrades. I came today to unit 208, opened up electrical panel read all voltage on breakers and the double pole 30 amp breaker was not getting any voltage on or off. I replaced the double pole 30 amp breaker, after direct connection from the a/c disconnect on roof it turned on for about 30-50 seconds and the breaker tripped once again. If you have questions or concerns, please give us a call. Your electrical technician, Xavier